|Home » Categories » Rockwell In-chassis » CompactLogix » MVI69 Series|
RSLogix 500 sample for MVI69-xxx faults MicroLogix processor
|Article Number: 211 | Rating: 5/5 from 1 votes | Last Updated: Tue, Jul 1, 2014 at 3:40 PM|
I/O mismatch the first versions of our MVI69-XXX sample for MicroLogix processors had the wrong vendor ID code defined under the I/O configuration.
Within the RSLogix 500 program change the vendor ID code from 22 to the correct vendor ID code of 309. This will correct the issue with the I/O mismatch between RSLogix 500 and the MVI69-XXX solution.
There are no attachments for this article.
My MVI69 module is not working. What might be wrong?
Viewed 3231 times since Fri, Oct 10, 2008
When using an MVI69-xxx or PS69-xxx module, why does a L43/L45 CompactLogix processor fault immediately after a download or after a power cycle?
Viewed 2728 times since Mon, Jan 18, 2010
IEC-60870-5-104 Server Tutorial
Viewed 3761 times since Mon, Sep 3, 2012
I have an In-Chassis module, and am seeing a type mismatch shown in the module properties. What is the issue?
Viewed 23772 times since Fri, Apr 27, 2007
Will ProSoft MVI69-xxxx solutions work with the new Allen-Bradley CompactLogix L23 series of processors?
Viewed 3017 times since Fri, Oct 31, 2008
Debug port connection parameters for Prosoft modules and gateways
Viewed 48941 times since Tue, Nov 28, 2006
Is the MVI69 series of ProSoft modules compatible with the MicroLogix1500 processor?
Viewed 19617 times since Tue, Nov 28, 2006