|Home » Categories » Rockwell In-chassis » CompactLogix » MVI69 Series|
RSLogix 500 sample for MVI69-xxx faults MicroLogix processor
|Article Number: 211 | Rating: 5/5 from 1 votes | Last Updated: Tue, Jul 1, 2014 at 3:40 PM|
I/O mismatch the first versions of our MVI69-XXX sample for MicroLogix processors had the wrong vendor ID code defined under the I/O configuration.
Within the RSLogix 500 program change the vendor ID code from 22 to the correct vendor ID code of 309. This will correct the issue with the I/O mismatch between RSLogix 500 and the MVI69-XXX solution.
There are no attachments for this article.
Will ProSoft MVI69-xxxx solutions work with the new Allen-Bradley CompactLogix L23 series of processors?
Viewed 2819 times since Fri, Oct 31, 2008
My MVI69 module is not working. What might be wrong?
Viewed 2974 times since Fri, Oct 10, 2008
Debug port connection parameters for Prosoft modules and gateways
Viewed 48635 times since Tue, Nov 28, 2006
The Wallclock in my ProSoft MVIxx-AFC module seems to be showing Greenwich Mean Time (GMT or Universal Time) instead of Local Time. How do I get it to use Local Time?
Viewed 1006 times since Wed, Dec 3, 2008
How do I completely remove a ProSoft Add-On Instruction (AOI) from a RSLogix5000 project?
Viewed 2451 times since Wed, Sep 28, 2011
How do I convert integer values to a floating point number in a Rockwell Controller?
Viewed 4138 times since Tue, Sep 7, 2010
Is the MVI69 series of ProSoft modules compatible with the MicroLogix1500 processor?
Viewed 19454 times since Tue, Nov 28, 2006
What are the differences between the MVI69-PDPS and PS69-DPS PROFIBUS slave modules?
Viewed 2065 times since Tue, Mar 24, 2009
IEC-60870-5-104 Server Tutorial
Viewed 2972 times since Mon, Sep 3, 2012
Converting integer values into a float or real data type when using a MicroLogix 1500.
Viewed 2319 times since Tue, Apr 27, 2010