|Home » Categories » Rockwell In-chassis » CompactLogix » MVI69 Series|
RSLogix 500 sample for MVI69-xxx faults MicroLogix processor
|Article Number: 211 | Rating: 5/5 from 1 votes | Last Updated: Tue, Jul 1, 2014 at 3:40 PM|
I/O mismatch the first versions of our MVI69-XXX sample for MicroLogix processors had the wrong vendor ID code defined under the I/O configuration.
Within the RSLogix 500 program change the vendor ID code from 22 to the correct vendor ID code of 309. This will correct the issue with the I/O mismatch between RSLogix 500 and the MVI69-XXX solution.
There are no attachments for this article.
When using an MVI69-xxx or PS69-xxx module, why does a L43/L45 CompactLogix processor fault immediately after a download or after a power cycle?
Viewed 2290 times since Mon, Jan 18, 2010
What are the power requirements for the MVI69 CompactLogix modules?
Viewed 20008 times since Tue, Nov 28, 2006
How do I convert integer values to a floating point number in a Rockwell Controller?
Viewed 3753 times since Tue, Sep 7, 2010
Is the MVI69 series of ProSoft modules compatible with the MicroLogix1500 processor?
Viewed 19397 times since Tue, Nov 28, 2006
Debug port connection parameters for Prosoft modules and gateways
Viewed 48520 times since Tue, Nov 28, 2006
How do I completely remove a ProSoft Add-On Instruction (AOI) from a RSLogix5000 project?
Viewed 2310 times since Wed, Sep 28, 2011
I have an In-Chassis module, and am seeing a type mismatch shown in the module properties. What is the issue?
Viewed 23219 times since Fri, Apr 27, 2007
What are Coldboot and Warmboot used for?
Viewed 60054 times since Tue, Nov 28, 2006
The Wallclock in my ProSoft MVIxx-AFC module seems to be showing Greenwich Mean Time (GMT or Universal Time) instead of Local Time. How do I get it to use Local Time?
Viewed 974 times since Wed, Dec 3, 2008
What are the differences between the PROFIBUS Master MVI69-PDPMV1 and PS69-DPM modules?
Viewed 2067 times since Tue, Mar 24, 2009