|Home » Categories » inRAx - Rockwell Platforms » MVI69 - CompactLogix|
RSLogix 500 sample for MVI69-xxx faults MicroLogix processor
|Article Number: 211 | Rating: 5/5 from 1 votes | Last Updated: Thu, Jan 17, 2008 at 12:00 AM|
|I/O mismatch the first versions of our MVI69-XXX sample for MicroLogix processors had the wrong vendor ID code defined under the I/O configuration. Within the RSLogix 500 program change the vendor ID code from 22 to the correct vendor ID code of 309. This will correct the issue with the I/O mismatch between RSLogix 500 and the MVI69-XXX solution.|
There are no attachments for this article.
Is the MVI69 series of ProSoft modules compatible with the MicroLogix1500 processor?
Viewed 19204 times since Tue, Nov 28, 2006
No matter what I do, I can't seem to get my MVI69 module working. What might be wrong?
Viewed 2272 times since Fri, Oct 10, 2008
What are the power requirements for the MVI69 CompactLogix modules?
Viewed 19588 times since Tue, Nov 28, 2006
I'm using the MVI69-GSC on a MicroLogix with the sample program, but when I try to put my own program on it I run out of memory space. Is there a smaller sample program?
Viewed 19607 times since Tue, Nov 28, 2006
What is the difference between the MVI69-MCM vs the MVI69-MNET?
Viewed 21230 times since Wed, Nov 29, 2006
Will ProSoft MVI69-xxxx solutions work with the new Allen-Bradley CompactLogix L23 series of processors?
Viewed 2213 times since Fri, Oct 31, 2008
When using an MVI69-xxx or PS69-xxx module, why does a L43/L45 CompactLogix processor fault immediately after a download or after a power cycle?
Viewed 1692 times since Mon, Jan 18, 2010
What are the differences between the PROFIBUS Master MVI69-PDPMV1 and PS69-DPM modules?
Viewed 1653 times since Tue, Mar 24, 2009
What are the differences between the MVI69-PDPS and PS69-DPS PROFIBUS slave modules?
Viewed 1570 times since Tue, Mar 24, 2009
Where can I get firmware for ProSoft products?
Viewed 2391 times since Thu, Aug 18, 2011