|Home » Categories » Rockwell In-chassis » CompactLogix » MVI69 Series|
RSLogix 500 sample for MVI69-xxx faults MicroLogix processor
|Article Number: 211 | Rating: 5/5 from 1 votes | Last Updated: Tue, Jul 1, 2014 at 3:40 PM|
I/O mismatch the first versions of our MVI69-XXX sample for MicroLogix processors had the wrong vendor ID code defined under the I/O configuration.
Within the RSLogix 500 program change the vendor ID code from 22 to the correct vendor ID code of 309. This will correct the issue with the I/O mismatch between RSLogix 500 and the MVI69-XXX solution.
There are no attachments for this article.
What are the power requirements for the MVI69 CompactLogix modules?
Viewed 20112 times since Tue, Nov 28, 2006
My MVI69 module is not working. What might be wrong?
Viewed 2968 times since Fri, Oct 10, 2008
What are Coldboot and Warmboot used for?
Viewed 60163 times since Tue, Nov 28, 2006
How do I completely remove a ProSoft Add-On Instruction (AOI) from a RSLogix5000 project?
Viewed 2439 times since Wed, Sep 28, 2011
How do I convert integer values to a floating point number in a Rockwell Controller?
Viewed 4094 times since Tue, Sep 7, 2010
Debug port connection parameters for Prosoft modules and gateways
Viewed 48622 times since Tue, Nov 28, 2006
I have an In-Chassis module, and am seeing a type mismatch shown in the module properties. What is the issue?
Viewed 23345 times since Fri, Apr 27, 2007
What are the differences between the PROFIBUS Master MVI69-PDPMV1 and PS69-DPM modules?
Viewed 2118 times since Tue, Mar 24, 2009
IEC-60870-5-104 Server Tutorial
Viewed 2949 times since Mon, Sep 3, 2012
Will ProSoft MVI69-xxxx solutions work with the new Allen-Bradley CompactLogix L23 series of processors?
Viewed 2814 times since Fri, Oct 31, 2008