|Home » Categories » Rockwell In-chassis » CompactLogix » MVI69 Series|
RSLogix 500 sample for MVI69-xxx faults MicroLogix processor
|Article Number: 211 | Rating: 5/5 from 1 votes | Last Updated: Tue, Jul 1, 2014 at 3:40 PM|
I/O mismatch the first versions of our MVI69-XXX sample for MicroLogix processors had the wrong vendor ID code defined under the I/O configuration.
Within the RSLogix 500 program change the vendor ID code from 22 to the correct vendor ID code of 309. This will correct the issue with the I/O mismatch between RSLogix 500 and the MVI69-XXX solution.
There are no attachments for this article.
The Wallclock in my ProSoft MVIxx-AFC module seems to be showing Greenwich Mean Time (GMT or Universal Time) instead of Local Time. How do I get it to use Local Time?
Viewed 986 times since Wed, Dec 3, 2008
How do I transfer a floating point value using integer files in a MicroLogix1500?
Viewed 18805 times since Thu, Apr 24, 2008
Is the MVI69 series of ProSoft modules compatible with the MicroLogix1500 processor?
Viewed 19418 times since Tue, Nov 28, 2006
When using an MVI69-xxx or PS69-xxx module, why does a L43/L45 CompactLogix processor fault immediately after a download or after a power cycle?
Viewed 2321 times since Mon, Jan 18, 2010
I have an In-Chassis module, and am seeing a type mismatch shown in the module properties. What is the issue?
Viewed 23267 times since Fri, Apr 27, 2007
IEC-60870-5-104 Server Tutorial
Viewed 2770 times since Mon, Sep 3, 2012
Debug port connection parameters for Prosoft modules and gateways
Viewed 48560 times since Tue, Nov 28, 2006
My MVI69 module is not working. What might be wrong?
Viewed 2925 times since Fri, Oct 10, 2008
Converting integer values into a float or real data type when using a MicroLogix 1500.
Viewed 2208 times since Tue, Apr 27, 2010
What are the differences between the MVI69-PDPS and PS69-DPS PROFIBUS slave modules?
Viewed 2017 times since Tue, Mar 24, 2009