|Home » Categories » Rockwell In-chassis » CompactLogix » MVI69 Series|
RSLogix 500 sample for MVI69-xxx faults MicroLogix processor
|Article Number: 211 | Rating: 5/5 from 1 votes | Last Updated: Tue, Jul 1, 2014 at 3:40 PM|
I/O mismatch the first versions of our MVI69-XXX sample for MicroLogix processors had the wrong vendor ID code defined under the I/O configuration.
Within the RSLogix 500 program change the vendor ID code from 22 to the correct vendor ID code of 309. This will correct the issue with the I/O mismatch between RSLogix 500 and the MVI69-XXX solution.
There are no attachments for this article.
The Wallclock in my ProSoft MVIxx-AFC module seems to be showing Greenwich Mean Time (GMT or Universal Time) instead of Local Time. How do I get it to use Local Time?
Viewed 975 times since Wed, Dec 3, 2008
IEC-60870-5-104 Server Tutorial
Viewed 2691 times since Mon, Sep 3, 2012
Debug port connection parameters for Prosoft modules and gateways
Viewed 48531 times since Tue, Nov 28, 2006
Is the MVI69 series of ProSoft modules compatible with the MicroLogix1500 processor?
Viewed 19405 times since Tue, Nov 28, 2006
How do I convert integer values to a floating point number in a Rockwell Controller?
Viewed 3767 times since Tue, Sep 7, 2010
My MVI69 module is not working. What might be wrong?
Viewed 2901 times since Fri, Oct 10, 2008
Converting integer values into a float or real data type when using a MicroLogix 1500.
Viewed 2164 times since Tue, Apr 27, 2010
What are Coldboot and Warmboot used for?
Viewed 60060 times since Tue, Nov 28, 2006
What are the differences between the PROFIBUS Master MVI69-PDPMV1 and PS69-DPM modules?
Viewed 2068 times since Tue, Mar 24, 2009
I have an In-Chassis module, and am seeing a type mismatch shown in the module properties. What is the issue?
Viewed 23230 times since Fri, Apr 27, 2007