|Home » Categories » Rockwell In-chassis » CompactLogix » MVI69 Series|
RSLogix 500 sample for MVI69-xxx faults MicroLogix processor
|Article Number: 211 | Rating: 5/5 from 1 votes | Last Updated: Tue, Jul 1, 2014 at 3:40 PM|
I/O mismatch the first versions of our MVI69-XXX sample for MicroLogix processors had the wrong vendor ID code defined under the I/O configuration.
Within the RSLogix 500 program change the vendor ID code from 22 to the correct vendor ID code of 309. This will correct the issue with the I/O mismatch between RSLogix 500 and the MVI69-XXX solution.
There are no attachments for this article.
My MVI69 module is not working. What might be wrong?
Viewed 3148 times since Fri, Oct 10, 2008
How do I transfer a floating point value using integer files in a MicroLogix1500?
Viewed 18936 times since Thu, Apr 24, 2008
Will ProSoft MVI69-xxxx solutions work with the new Allen-Bradley CompactLogix L23 series of processors?
Viewed 2971 times since Fri, Oct 31, 2008
I have an In-Chassis module, and am seeing a type mismatch shown in the module properties. What is the issue?
Viewed 23671 times since Fri, Apr 27, 2007
The Wallclock in my ProSoft MVIxx-AFC module seems to be showing Greenwich Mean Time (GMT or Universal Time) instead of Local Time. How do I get it to use Local Time?
Viewed 1112 times since Wed, Dec 3, 2008
What are Coldboot and Warmboot used for?
Viewed 60478 times since Tue, Nov 28, 2006
How do I convert integer values to a floating point number in a Rockwell Controller?
Viewed 5554 times since Tue, Sep 7, 2010
Debug port connection parameters for Prosoft modules and gateways
Viewed 48853 times since Tue, Nov 28, 2006
Converting integer values into a float or real data type when using a MicroLogix 1500.
Viewed 2664 times since Tue, Apr 27, 2010
What are the power requirements for the MVI69 CompactLogix modules?
Viewed 20310 times since Tue, Nov 28, 2006